Company: Henan Lubao Special Cable Co., Ltd.
Contact: Manager Su
Address: No. 13 Workshop B, Tiantan Venture Park, Huling Industrial Gathering District, Jiyuan City, Henan Province
Uo / U is 0.6 / 1Kv and below
GB / T12527-2008
This product is suitable for overhead wires and cables under rated voltage 0.6 / 1KV
Overhead insulated cables with a rated voltage of 1kV and below
This product is suitable for copper core, aluminum core or aluminum alloy core weather-resistant PVC, polyethylene and XLPE insulated overhead lines for overhead power lines with AC rated Uo / U of 0.6 / 1KV and below
Conditions of Use
Working temperature: polyethylene, polyvinyl chloride below 70 degrees Celsius, cross-linked polyethylene insulation does not exceed 90 degrees Celsius.
Rated voltage: 0.6 / 1KV or less
Cable laying temperature: not lower than minus 20 degrees Celsius
Allowable bending radius of cable: those with cable outer diameter (D) less than 25MM, no less than 4D, and those with cable outer diameter 9 (D) of 25MM or more, no less than 6D.
JKV copper core PVC insulated aerial cable
JKLV aluminum core PVC insulated aerial cable
JKLHV aluminum alloy core PVC insulated aerial cable
JYK copper core polyethylene insulated aerial cable
JKLY aluminum core polyethylene insulated aerial cable
JKLHY aluminum alloy core polyethylene insulated aerial cable
JKYJ copper core XLPE insulated aerial cable
JKLYJ aluminum core XLPE insulated aerial cable
JKLHYJ aluminum alloy core XLPE insulated aerial cable
The above are 0.6 / 1KV voltage level overhead fixed laying, household line, etc.